Dec 08, 2017 12:15 pm
I am about to install some Hunter MP1000 mp rotator pop up sprinklers and am hoping people can post how they installed them and what I need to consider? For example the pipe that connects them do I use greenline, blueline or PVC pressure pipe glued and what diameter works best for fittings? Also what kind of box do I install the solenoids and valve into and what brand of solenoids are reliable? What about the controller, do any work well in a smart home environment as I use Openhab as my server? Any links to guides that show how it all goes together?
Any tips and info or brands to choose would be great.
Re: Popup sprinkler help needed2
Dec 24, 2017 11:14 am
Since I got no replies, I'll add some info I found to help others...
The trencher I hired did not do straight runs due to one tyre being worn, so I opted to use what is called 1" Low Density Poly pipe as it bends around corners and is forgiving if people stand or drive on the popups. Using articulated risers from PVC added complexity and cost and makes installation harder. Cost of the pipe is around $1 per meter and the fittings are cheap usually around $1 each. I used stainless steel clips to hold the pipe to the fittings made by Norma and they seem to work very well and the shops say they are far better than plastic clips. They can be reused and just click when squeezed.
The shop helped design the system for me and recommended I use 11 of the MP2000 in non presure regulated bodies and spaced 5m apart which has worked well as I have tons of flow and pressure. Having a shop go over my details was handy as otherwise I would have purchased pressure regulated popup bodies which cost 3 times as much. I have 500 Kpa and 50 Litres per minute flow rate as my house is right on a major water main and I have used 32mm Metric poly pipe as the feed to the valve box to ensure friction loss is low. Without that flow I dont think 11 rotators on a single zone would be a good idea but the shop told me I had 35 L/min to use before pressure would cause issues and I am only using 32 L/min and the popups are installed and working well.
Sign in or Join to reply to this Topic
building-expertfoundation damage on faulty sprinklerfoundation damage on faulty sprinkler
Any good building consultant should be able to inspect and prepare a report for you. If you did not have independent inspection during construction it makes sense to have…
Homeone1234Faulty sprinkler timer cause foundation damage?Faulty sprinkler timer cause foundation damage?
Hello guys, The builder installed a faulty sprinkler timer causing water to run continuously for uncertain period of time in the front lawn during construction. The water…
langkawanHelp needed with lightings location please.Help needed with lightings location please.
As my builder uses Clipsal, I think I just wanna stick to that as we're going to start building very soon. But I looked in the Clipsal website and found some that are…