Jul 29, 2017 6:47 pm
I would love some advice guys and girls -
I dug a hole at my place about 40 cm down to find my home copper water pipe which is capped for a future shed. The pipe comes out from the house and under a new concrete path. My hole was not far from the path.
It hasn't rained much in the past 2 weeks and the soil is mostly clay.
The top was hard and dry.
About 30cm deep the ground became so soft and wet i barely needed the shovel. It was here i found the pipe.
It doesn't appear to be gushing out water but it could be a leak under the concrete further along?
I'm hoping you guys will tell me clay holds water underground or disturbed clay will still be wet (as it was only installed under 2 months ago).
More info: I dug another hole further away from the pipes and it was not as wet but still moist.
I dug a hole further than that and it was dry.
Worst case scenario it could be a leak coming out from under the concrete possibly from when the concrete path was installed the path 1 month ago.
Re: Need urgent advice about clay soil holding water vs a le2
Jul 29, 2017 7:16 pm
Did you say the trench for the water pipe was only dug two months ago? If so the trench could still be wet from the backfilled clay, especially if it was not compacted in layers when reinstated.
Regards James Mason
Re: Need urgent advice about clay soil holding water vs a le5
Jul 30, 2017 12:06 am
The trench that the pipe is in will have uncompacted soil along its length and act as a conduit. This is why houses built on highly reactive soil are required by AS 2870 to have clay plugs in the service trenches to prevent water using those trenches as conduits and flowing under the house.
Re: Need urgent advice about clay soil holding water vs a le8
Jul 30, 2017 2:10 pm
Unfortunately we don't have a Meter we are on tank water
If the line is connected to the pump feed, a leak would make the pump cycle.
Re: Need urgent advice about clay soil holding water vs a le10
Jul 30, 2017 5:43 pm
As soon as the pressure controller registered the cut in pressure setting, the pump would start and recharge the line. Water is not compressible unless you have a handy black hole nearby, it doesn't take much fluid loss to lower the pipe's static pressure to the pressure controller's cut in pressure setting. Having a pressure tank would disguise it but the pump would also run for longer.
Sign in or Join to reply to this Topic
knhchrisIs it possible for me to do this water leak job?Is it possible for me to do this water leak job?
Hi all, Thank you for all your replies. I have applied a silicone as a temporary fix. It has been working so far. I definitely agree with getting a professional to do…
arcadeltWater leak through window frameWater leak through window frame
First thing is to take the blind down so it doesn’t get damaged, and anything else under the leak that is getting wet. Unless there is a leak from a pipe in the wall…